NOTE: Please be sure to check your email's Spam or Junk folder since our responses may land there the first time you hear from one of our project managers.
E84 2-Ply 20oz OSNA
Report of Testing “20 oz. vinyl wall covering with fabric backing” for compliance with the applicable requirements.
Report of Testing “20 oz. vinyl wall covering with fabric backing” for compliance with the applicable requirements of the following criteria: ASTM E84-16 TEST FOR SURFACE BURNING CHARACTERISTICS OF BUILDING MATERIALS (UL 723, UBC 8-1, NFPA 255)
The specimen was prepared by Intertek technicians on March 31, 2017 at Intertek Laboratories located in Elmendorf, TX. The specimen was described by the client as “Lot 189682”. The 24 ft. long test specimen consisted of three 8 ft. sections of wall covering material adhered to 1/4 in. thick cement board. The product was received by our personnel in good condition and given an identification number of SAT1703141139-001.
The specimen was self-supporting. The finished side was exposed towards the flames.
The test results, computed on the basis of observed flame front advance and electronic smoke density measurements are presented in the following table.
|Test Specimen||Flame Spread Index||Smoke Developed Index|
|20 oz. vinyl wall covering with fabric backing||20||95|
During the test, the specimen was observed to behave in the following manner.
|0:00||The test burners were turned on.|
|0:11||The wall covering began to blister|
|0:13||The wall covering began to melt.|
|0:14||Steady ignition was observed.|
|0:51||The wall covering began to flake.|
|0:53||Small burning chunks began to fall.|
|10:00||The test burners were shut off.|
After the test, the specimen was observed to be damaged as follows:
|0-7||The wall covering was observed to be consumed.|
|7-10||The wall covering was observed to be partially melted and heavily charred.|
|10-24||The wall covering was observed to be heavily discolored and blistered.|
Flame Spread Index: 20
Smoke Developed Index: 95
Time to Ignition (sec): 42
Time to Max FS (sec): 98
Maximum FS (feet): 4.6
Time to 980 F (sec): Never Reached
Time to End of Tunnel (sec): Never Reached
Max Temperature (F): 551
Time to Max Temperature (sec): 569
Total Fuel Burned (cubic feet): 44.21
FS*Time Area (ft*min): 40.2
Smoke Area (%A*min): 65.9
Unrounded FSI: 20.7
- This test sample meets the A.S.T.M. E84-16 Standard.
Test performed and certified by: